We occasionally encounter some situations, such as: the load pulls down the output voltage of each phase, so that the output voltage needs to be adjusted.
After the customer installs our three-phase inverter, if one phase of the inverter's output voltage deviates from your local voltage, how to adjust to the correct voltage,please continue to look down:
It is easy,just have 2 step:
If the inverter is a three-phase 380V, when the A-phase output deviates from the local voltage
The first step:use a multimeter to clamp the A Phase and 0 line of the output at the same time(A phase means R).If there is a deviation in the B phase, the B phase and the 0 line are clamped;(B phase means S)
The second step:Do not let go of the clip, then test the potentiometer of the main board on the top of the inverter, turn the small switch on the potentiometer with a screwdriver, and watch the multimeter debug to 220V.(If the inverter is three phase 220V,here we need to watch the multimeter debug to 110V)
New Technology of the 200kw inverter: warm backup The warm backup is a method of backing up a database using the archivelog mode when the database is running.
Why did the customer choose our company's products finally?Because the quality of other companies ’solar inverter is not as good as ours. Our solar inverter are from production to after sales the one-stop service. After strict control and testing the prod